Switched receptacle wiring diagram
These electrical wiring diagrams show typical connections. The diagram below shows the power entering the circuit at the grounded outlet box location, then sending power up to the switch and a
switched leg back down to the outlet. Wiring a Split Switched Outlet with a Switch Loop. This diagram illustrates the wiring for a split half outlet controlled with a switch loop. The tab connecting the hot terminals on the
receptacle is removed and the source hot is connected to the bottom half. These wiring diagrams show typical connections. The diagram above shows the power entering into the circuit at the switch box location, then sending one power line for the dishwasher and a switched leg for the garbage disposal. Wiring Diagram for Dual Outlets. Here 3-wire cable is run from a double-pole circuit breaker providing an independent 120 volts to two sets of multiple outlets. The neutral wire from the circuit is shared by both sets. This wiring is commonly used in a 20 amp kitchen circuit where two appliance feeds are needed, such as for a refrigerator and a microwave in the same location.
®SPECIFICA AL Page ob Name: ob Number: Model Numbers: Vive PowPak 20 A Receptacle Control Relay Module Wireless Receptacle Control Specifications 369966d 2 03.07.17 Regulatory Approvals A half-hot (or switched) outlet is a double outlet that has one half permanently on (ready to provide electricity) while the other half can be turned on and off via an ordinary wall switch. Energy requirements for controlling 50% of the receptacles in commercial buildings can be achieved in two different ways: • Split-wired receptacles (shown in Diagram 1)—one plug on each receptacle is controlled • Duplex receptacle (shown in Diagram 2)—one receptacle within 6 feet of each uncontrolled receptacle is controlled In the previous article " Branch Circuit
Design Calculations – Part One " in our new course " Course EE-3: Basic Electrical design course – Level II ", I indicated that Branch-circuit are classified According To Type of Load into five categories: Lighting Branch circuit, Receptacle Branch circuit, Equipment Branch circuit, Heating and cooling loads Branch circuit, Here shows what reading you should get from neutral to ground under normal conditions. This is a line diagram to help simplify the circuit. Checking from neutral to ground in these normal conditions should read at or near zero volts. KeyMaster Systems Hardware Installation Guidelines Wiring RS-485 Networks Wiring Controlsoft RS-485 networks Operation Controlsoft RS-485 access control …